- Country of manufactureUkraine
room dimensions: 6000x4000x2500(H) mm.;
- temperature in shop – +12 … +14 0C;
- air temperature surrounding the room no more than +25 0C;
- stitched air temperature – no more than +18 0C;
- number of at the same time working people – to the 2nd persons;
- settlement refrigerating capacity – 5,6 kW;
- boiling temperature – +2 0C;
- coolant type – R507A (which is not containing chlorine, ozone-safe);
- quantity of air coolers – one;
- operating time of refrigerating appliances – 20 h/days.
- air temperature in the location of portable refrigerating appliances – to + 350C;
- coefficient of a stock of potrebny refrigerating capacity – 10%;
The medium temperature independent compressor and condenser DANFOSS-OPTYMA unit (on the basis of the tight piston compressor), necessary hladonovy fittings and devices of automatic equipment, a control panel with the electronic DANFOSS controller is a part of the refrigeration unit.
In shop of a boning it is supposed to place a ceiling air cooler with an air ottayka and a low consumption of ECO LUVATA air.